GROUNDING TECH BULLETIN
You need a good ground both for
the operation of telephone and computer equipment,
as well as to prevent damage from surges over the power, phone and data lines...
For voice and data we manufacture what we call Maximum Lightning
Protection (MLP) surge protectors. Unfortunately
most of our customers buy them after their stuff has blown up.
In a nutshell a modern voice and data lighting protector has two stages of protection:
- It takes voltages over a certain level and
sends them to ground. That's mostly what damages phone and computer
- It takes current over a certain level and
opens a self resetting fuse (like a self-resetting circuit-breaker). That
often comes into play when a power line shorts to a phone or data pair. Not
Since most damage is caused by high voltage,
which a protector sends to ground, if you don't have a good ground you don't
have lightning protection - even if you bought the best you could find (ours!).
In a place like Chicago where there is ordinary dirt
almost everywhere a good ground is pretty easy to get. The electrician drives an
8 foot ground rod into the dirt right outside where the main circuit-breaker
panel is and runs a heavy gauge wire from the ground rod to the metal box for
The ground is then carried to all the outlets in the
building through the conduit attached to the metal circuit-breaker box, through
the green ground wire put in most conduits (usually not for light switches), and
on the ground wire in Romex when the local authorities don't require conduit.
Sometimes the electrician forgets to attach the big gauge
wire to the ground rod or to the metal box inside. If you're not sure, it's
worth going to look for your ground rod to see if the wire (or big braided wire)
is attached - or just hanging loose?
The real problem comes when the earth around a building
isn't just plain dirt. If it's rocks, gravel, sand or clay, those
materials don't conduct electricity as well as nice moist dirt - and you have a
Sometimes the best way to find a grounding expert in your
area is to ask the chief engineer at a local radio station. They need a really
good ground for their antenna and may know a local expert.
If you have rocky or sandy soil, the
ground is just as important for protecting the AC to your equipment as it is to
the telephone lighting protectors.
For lightning protection you want as short a ground wire
as possible from the electrical panel to your surge protectors. You want to make
as few turns (changes in direction) as possible, and the wire shouldn't make a
hard "right angle" turn. It should have a six inch or so radius to the turn.
Lightning can jump out of a right angle bend in a ground
wire to another wire or piece of equipment. For that reason, you never want to
have unprotected pairs on the same block (like a 66 block) as protected pairs.
The phone company is supposed to put in lighting
protection before the phone lines enter a building. This is usually the cheapest
form of lighting protection, usually sufficient to protect a user talking on the
phone in a lightning storm (not a great idea) on an old non-electronic single
line phone (like a 2500 set).
Unfortunately the phone company ground is often missing,
not connected, or otherwise just bad - so you shouldn't count on there being any
protection at the phone company's Network Interface. There's nothing you can do
to fix that ground yourself (unless it's obviously just not connected
somewhere). The phone company may come out and check it for you if you ask them,
but the technician may not know how to check it anyway?
You do want the phone company's lightning protection to be
working since there is a possibility that the lightning would get into the walls
in the building and start a fire - which was why lighting protectors were
originally put on phone lines entering wooden structures over a hundred years
ago. They probably saved quite a few humans from getting toasted talking on the
phone through the
In the old days a cold water pipe was considered the best
ground. That was because the metal water main was buried in the earth before it
got into the building and continued uninterrupted anywhere in the building that
there was cold water. Hot water, gas pipes or fire sprinkler systems were never
a good choice since there could be equipment insulating the pipes before the
pipes go into the ground.
Since the development of PVC plastic pipes, cold water is
considered a horrible idea even if the pipes you can see are metal, since at
some point it could make a transition to or from metal / plastic. Plastic will
never conduct electricity well enough to give you any kind of
A bad ground could easily be caused by someone doing work
in the building and disconnecting the ground anywhere along the run. You just
can't assume anything with a ground.
So what will happen if you have a bad ground? You could
have strange problems with telephone and computer equipment, but the most
expensive thing could be if the surge continues through your lightning protector
into your electronic equipment, blowing it up.
Without a good ground the closest thing to ground is your
power line. So instead of the surge going to ground (which either isn't there or
looks like less of a ground than the electronic equipment), it goes into the
electronic equipment and blows it up.
If you have good lightning protection and your stuff
keeps getting blown up it's time to start getting your ground checked out.
If the electronic equipment is too far from the main metal
electrical panel, it may be better these days to use the third prong ground in
an outlet. To do that, you need to test the outlet with an outlet checker.
If the outlet tester says your ground is OK, the green
wire coming from the electrical panel to that outlet may be the best way to get
a ground to a lighting protector?
We manufacture two versions of a special 10 foot ground
wire. It has a yellow 3 prong plug, with a green #12 or #10 ground wire.
You definitely don't want to plug it into a power strip.
Plug it directly into the outlet. You want as little resistance as possible to
get the surge to earth.
Without a good ground on the outlet a computer type surge
protector or battery backup isn't going to give you much AC protection. Since
your phone equipment connects to both AC and the phone or data lines you want to
to protect all of those connections.
Click HERE to see
our various models of Lighting Protectors for Voice and Data
Static electricity is a problem in the winter all over the US. Without a good
ground on your phone system or computer equipment the high voltage static shock
has to go through your equipment to get to the power line, which is the closest
thing to ground.